Can I use a 3 pole MCCB on a single phase system?
Yes. LS UL489 Molded Case Circuit Breakers (MCCB’s) are suitable for use in single phase systems. LS Susol UTE/UTS 3 pole MCCBs may be applied to single phase systems provided that the MCCB is sized appropriately per the given load. Furthermore, ...
VFD Capacitor Reforming Guide
1. About Reforming Capacitors Ensure that capacitors are reformed once a year when stored with the power off. If drives have been stored and non-operational for more than a year, capacitors may get damaged when operating the drive under load. When ...
How do I reset my VFD to factory default?
Resetting, initializing, or factory defaulting a VFD puts all of the parameters back to the default settings. This can be used when you want to start the programming from scratch. This is done with one parameter. See the below procedure. Procedure ...
How does the M100 and G100 connect to DriveView?
The M100 and G100 have a couple options for connecting to DriveView 9 software. When using either of the below cables your baud rate in Driveview 9 should match the baud rate on the VFD set at CM.03 Be sure to set the connection type to "Modbus-RTU" ...
H100+ Lead Lag Setup
H100+ drives have a built-in, lead-lag function which allows for redundant motor control using multiple drives with multiple pumps. Also known as "master-follower" or "lead-lag loadshare", this works without the use of an externally controller such ...