Can I use a 3 pole MCCB on a single phase system?
Yes. LS UL489 Molded Case Circuit Breakers (MCCB’s) are suitable for use in single phase systems. LS Susol UTE/UTS 3 pole MCCBs may be applied to single phase systems provided that the MCCB is sized appropriately per the given load. Furthermore, ...
VFD Capacitor Reforming Guide
1. About Reforming Capacitors Ensure that capacitors are reformed once a year when stored with the power off. If drives have been stored and non-operational for more than a year, capacitors may get damaged when operating the drive under load. When ...
How does the M100 and G100 connect to DriveView?
The M100 and G100 have a couple options for connecting to DriveView 9 software. When using either of the below cables your baud rate in Driveview 9 should match the baud rate on the VFD set at CM.03 Be sure to set the connection type to "Modbus-RTU" ...
G100/S100 will not start after power loss
By default, as a safety precaution, the VFD will not start after a momentary or extended power loss without cycling the RUN command. Adjusting the below listed parameters will fix this issue. Required Settings Ad/ADV.10=1 -Yes Cn/CON.71=0100 See ...
Setting up PID on an H100 VFD
PID (which stands for Proportional, Integral, and Derivative) control is a process control loop used to regulate a variable such as temperature or pressure. In terms of VFDs, this is usually accomplished with a transducer that provides feedback to ...